Cummins 1125 kva Silent Gensets
1125kva silent gensets Gensets’s Parameter Chongqing Sanchai Power Group,the predecessor is Chongqing Sanchai Engine Manufacture Co., Ltd. Established in 2009, now located in Tongliang Industrial Park of Chongqing. China"Sanchai" mainly engages in research, development, design,...
1125kva silent gensets
The method of correctly using the silent generator set is as follows: There are three main types:
First, pay attention to the manual operation of the silent generator set:
1. Check whether the fuel, oil and cooling water are proper before starting manually. Insufficient should be replenished in time. The unit should be free from oil leakage and water leakage.
2. The automatic control button of the automatic controller should be set to the middle position.
3. Open the key of the start circuit, continue to twist the key to the right to start the diesel engine. After the start is successful, return the key to the charging position.
4. After the machine is stopped, the key should be promptly dialed back to the middle position.
Second, the silent diesel generator set automatic operation:
1. Under normal conditions of the mains, turn the automatic control button of the automatic controller up to the "automatic" position. Manual start of the diesel engine is prohibited at this time. When the utility power is cut off, the diesel generator set can be automatically started and automatically supplied to the grid via the ATS switch.
2. After the unit starts up automatically, the key switch should be turned to the charging position in time.
3. After the mains call, the unit can stop automatically. After the machine is stopped, the key switch should be turned to the middle position to prevent the battery from being powered down and affect the next use.
Third, maintenance, maintenance:
1. After the new machine is running for 60 hours, it needs to change the oil, clean the diesel filter and air filter.
2. The electrolyte of the battery should be checked frequently. When it is insufficient, it should be replenished in time.
3. Always check the tightness of the belt, adjust the tensioning mechanism, and maintain the tension.
4. In the cold season, the water heating and oil heating switch should be turned on to keep the unit at a certain temperature to ensure that the unit can be used normally.