Diesel generator sets should be left around 1 meters space, the water tank end according to the size of the tank core retained ventilation window. This requirement is the minimum size of the machine room, the user can increase according to the need.
The foundation of the diesel generator set should be built on the hard land surface, tamping, make the 200mm thick concrete ground, the ground should be flat.
Users in the construction of the computer room, should be in the top of the roof of the unit to be embedded lifting steel beams for future maintenance.
The room should be well ventilated and the ground should be flat and non-slip.
Unit exhaust pipe diameter should not be smaller than the diesel exhaust port diameter, bending pipe should not be more than 3, bending angle should be greater than 90 degrees, the exhaust pipe should be supported or hoisting bracket to ensure that the unit muffler, supercharger and other forces.
The room should be equipped with fire extinguishers and other tools.
Related Industry Knowledge
- Overview of generator Sets
- Applicable scope and basic principle of diesel ...
- Periodically check the performance of the gener...
- Characteristics of silent Generator set
- Noise reduction facilities for silent diesel ge...
- Power calibration of Diesel Generator set
- Main uses of generator sets
- Advantages of Diesel Generator sets
- Purchase of diesel Generator set
- How to change the oil of diesel generator set c...
- How to deal with common faults of diesel genera...
- The exhaust black smoke of diesel generator
- Diesel engine power shortage causes and solutions
- Generator set daily maintenance
- What components does the generator set consist of?
- Marine diesel generator set
- The reason why the diesel engine burns the tile